Utah Administrative Code
The Utah Administrative Code is the body of all effective administrative rules as compiled and organized by the Division of Administrative Rules (Subsection 63G-3-102(5); see also Sections 63G-3-701 and 702).
NOTE: For a list of rules that have been made effective since February 1, 2015, please see the codification segue page.
NOTE TO RULEFILING AGENCIES: Use the RTF version for submitting rule changes.
R432. Health, Family Health and Preparedness, Licensing.
Rule R432-13. Freestanding Ambulatory Surgical Center Construction Rule.
As in effect on February 1, 2015
Table of Contents
- R432-13-1. Legal Authority.
- R432-13-2. Purpose.
- R432-13-3. General Design Requirements.
- R432-13-4. General Construction, Patient Facilities.
- R432-13-5. General Construction.
- R432-13-6. Extended Recovery Care Unit.
- R432-13-7. Exclusions to Guidelines.
- R432-13-8. Penalties.
- Date of Enactment or Last Substantive Amendment
- Notice of Continuation
- Authorizing, Implemented, or Interpreted Law
This rule is adopted pursuant to Title 26, Chapter 21.
The purpose of this rule is to establish construction and physical plant standards for the operation of a freestanding surgical facility that provides surgical services to patients not requiring hospitalization.
(1) Ambulatory Surgical Centers shall be constructed in accordance with the requirements of R432-4-1 through R432-4-23 and the requirements of the Guidelines for Design and Construction of Health Care Facilities, Sections 3.1 and 3.7, 2010 edition (Guidelines). Where a modification is cited, the modification supersedes conflicting requirements of R432-4 or the Guidelines.
(2) Ambulatory Surgical Centers shall consist of at least two Class C operating rooms, meeting the requirements of Guidelines section 3.7-3.3.4, and support facilities.
(3) Ambulatory Surgical Centers shall be equipped to perform general anesthesia. Flammable anesthetics may not be used in Ambulatory Surgical Centers.
(4) Ambulatory Surgical Centers shall comply with NFPA 101, Life Safety Code, Chapter 20.
(5) The facility shall have at least two exits leading directly to the exterior of the building.
(6) Design shall preclude unrelated traffic through units or suites of the licensed facility.
(1) Adequate sterile supplies shall be maintained in the facility to meet the maximum demands of one day's case load.
(2) Operating rooms for cystoscopic procedures shall comply with Section 2.2-184.108.40.206 of the Guidelines.
(3) A toilet room shall be readily accessible to recovery rooms and recovery lounge.
(4) Special or additional service areas such as radiology, if required by the functional program, shall comply with the requirements of the General Hospital Rules, R432-100.
(1) The administration and public areas which are not part of the Ambulatory Surgical Center exiting system, may be located outside of the institutional occupancy envelope when authorized by the local building official having jurisdiction.
(2) Cubicle curtains and draperies shall be affixed to permanently mounted tracks or rods. Portable curtains or visual barriers are not permitted.
(3) An elevator shall be provided when an ambulatory surgical center is located on a level other than at grade. The minimum inside dimensions of the cab shall be at least 5'8" wide by 8'5" deep with a minimum clear door width of 3'8".
(4) Yard equipment and supply storage areas shall be located so that equipment may be moved directly to the exterior without passing through building rooms or corridors.
(5) The facility shall provide for the sanitary storage and treatment or disposal of all categories of waste, including hazardous and infectious wastes, if applicable, using procedures established by the Utah Department of Environmental Quality and the local health department having jurisdiction.
(6) All rooms shall be mechanically ventilated.
(7) Access to medical gas supply and storage areas shall be arranged to preclude travel through clean or sterile areas. There shall be space for enough reserve gas cylinders to complete at least one routine day's procedures.
(8) An on-site emergency generator shall be provided and the following services shall be connected to the emergency generator:
(a) life safety branch as defined in 517-32 of the National Electric Code NFPA 70;
(b) critical branch as defined in 517-33 of the National Electric Code NFPA 70;
(c) equipment system as defined in 517-34 of the National Electric Code NFPA 70.
(9) There shall be sufficient fuel storage capacity to permit at least four hours continuous operation shall be provided.
(10) Lighting shall comply with R432-4-23(21)(a).
(1) A facility that provides extended recovery services shall maintain a patient care area that is distinct and separate from the post-anesthesia recovery area. The patient care area shall provide the following:
(a) a room or area that ensures patient privacy, including visual privacy;
(b) a minimum of 80 square feet of space for each patient bed with at least three feet between patient beds and between the sides of patient beds and adjacent walls.
(c) a nurse call system at each patient's bed and at the toilet, shower and bathrooms, which shall transmit a visual and auditory signal to a centrally staffed location which identifies the location of the patient summoning help;
(d) a patient bathroom with a lavatory and toilet;
(e) oxygen and suction equipment;
(f) medical and personal care equipment necessary to meet patient needs.
(2) A separate food nutrition area which shall include a counter, sink, refrigerator, heating/warming oven or microwave, and sufficient storage for food items.
The following sections of the Guidelines do not apply to Freestanding Surgical Center construction:
(1) Waste Management Facilities, Section 3.1-5.4.
The Department may assess a civil money penalty of up to $10,000 and deny approval for patient utilization of new or remodeled areas if a health care provider does not submit architectural drawings to the Bureau of Licensing. The Department may assess a civil money penalty of up to $10,000 if the licensee fails to follow Department- approved architectural plans. The Department may assess a civil money penalty of up to $1,000 per day for each day a new or renovated area is occupied prior to licensing agency approval.
health care facilities
February 21, 2012
April 1, 2014
For questions regarding the content or application of rules under Title R432, please contact the promulgating agency (Health, Family Health and Preparedness, Licensing). A list of agencies with links to their homepages is available at http://www.utah.gov/government/agencylist.html or from http://www.rules.utah.gov/contact/agencycontacts.htm.